Model Description: APCRBC140 Battery Cartridge Replacement
Compatibility: SURT3000RMXL, SURT3000RMXLT, SURT3000XLI, SURT3000XLT, SURT3000XLTW, SURTA3000RMXLT, SURTA3000XLT, SURT5000RMXLI, SURT5000RMXLI, SURT5000XLI, SURT5000XLT, SURT5000XLTW, SURT6000RMXLI, SURT6000RMXLT, SURT6000XLI, SURT6000XLT, SURT6000XLTW, SURT7500RMXL, SURT7500RMXLT, SURT7500XLI, SURT7500XLT, SURT7500XLTW, SURT8000RMXLI, SURT8000RMXLT, SURT8000XLI, SURT8000XLT, SURT8000XLTW, SURT10000RMXLI, SURT10000RMXLT, SURT10000XLI, SURT10000XLT, SURT10000XLTW
Condition: Fresh new batteries, clean system pulled trays
Includes: RBC14 Battery Cartridge (plug and play installation) - Each RBC140 consists of 2 Battery Modules (as in the photo)
Warranty: 1 year full replacement warranty included, additional warranty is available
Life time expectancy: 3-5 years
Manufacturer: UPS Battery Center Ltd.
The APCRBC140 replacememt battery cartrige is made with high quality UPS Rated batteries that are designed to provide excellent performance and long life in mission critical UPS devices. This battery packs meets and exceeds original manufacturer specifications.
Our batteries are new and always fresh stock. TheAPCRBC140 replacement battery cartridge is covered by our industry leading 1 year replacement warranty. Extended warranty of up to 3 years is available for your convenience. Our warranty is inclusive of shipping costs and is hassle free, the only warranty of this kind in the marketplace.
The APC Replacement Battery Cartridge #140 arrives assembled and ready for use. No assembly is required. Installation is plug and play, Smart-UPS RT units offer hot swap functionality.
Frequently Asked Questions:
How many battery modules are included with (1) APCRBC140?
Each APCRBC140 Replacement set consists of (2) battery modules, as seen in the picture
My APC Smart-UPS RT 8000 has 4 battery trays inside, how many RBC140's do I need?
The RBC140 consists of two trays (two battery modules), for your system you would need (2) RBC140's.
Do I need to shut down my UPS to replace the RBC44's?
No, the RT's have hot swap capability. You can swap the battery modules without shutting down the UPS. While the battery modules are out of the UPS, there will be no battery run time protection.
Can I replace one of the two battery modules?
No, both battery modules, (1) complete RBC140 needs to be replaced at a time.
How do I dispose of my old battery modules?
In the box with the new RBC140, there will be a prepaid shipping label to send the old/spent battery modules off for recycling.
How many RBC140's are needed for a SURT192XLBP Battery Pack?
The SURT192XLBP extended run time battery cabinet requires (2) RBC140's.
I am getting an error on my APC Smart-UPS RT 10000 "Critical - UPS: At least one faulty battery exists.", we have several external battery packs as well. How do I know exactly which RBC140 is faulty?
There is no easy way to know exactly which set of batteries had the failure. If you purchased the UPS and the battery packs at the same time, they will all start failing around the same time. It is highly recommended to replace all of the battery packs at once. This will provide the longest run time and most reliable performance. The only way to determine which set failed is to test each set individually. Disconnect all of the external batteries and test each APCRBC140 set to see if it gets the error from the system.